Enclosed Flooding FM200 Fire Suppression System For Multiple Rooms
|2||Scale of Protective region for one zone||area:max single-zone is 800m² volume:max single-zone is 3600m³|
|6||Nitrogen Pressure of Driving Device||6.0±1.0Mpa(20℃)|
|7||Condition of reserving room for container||temperature: -10~50℃, relative humidity: ≤97%|
|8||max working pressure||5.3Mpa|
|9||min working pressure||4.2Mpa|
Fm200(htc-227ea) is a kind of colorless and tasteless and
non-corrosive and electricity-insulating gas without residue and
pollution after extinguishing. And ODP of it is zero. It is a
friendly-environment gas to be used for extinguishing. Also,
because of such feature, it can be used in special place where
electrical fire is easy to happen.
Management of Multiple zones is also in the safe control of the
whole system. We can use one system to protect multiple zones
through selective valves. It can let the whole system alternative
aiming at different protective zone. Agent can be discharged into
where the fire happens. It will be very efficient to put out fire
in short time. One thing that need to mention, is that a little
room should be prepare to be as storage space for the whole system.
Electronic computer room, a data processing center,
telecommunications facilities, process control, expensive medical
equipment, industrial equipment, library, museum and art gallery,
clean room, flammable liquid storage area, etc.
The place where the fire is easy to happen, like paint-spraying
production line, aging-electrical equipment, rolling machine,
printing machine, oil switch, oil immersed transformer, melt
impregnating tank, tank, large generators, drying equipment, cement
production process of pulverized coal, and the ship's engine room,
cargo hold, etc.
4.2Mpa Fm200 System Used For Multiple Rooms Control is mainly
composed by three parts. Extinguishing devices and pipe fittings
and electrical accessories.
Extinguishing devices are such things, like cylinder to fill and
store fm200, frame and driving device(nitrogen cylinder) to trigger
the storage cylinder to discharge agent and so on.
Pipe fittings are those conduits to connect extinguishing device
and guide agent into protective zone, like high pressure galvanized
steel pipe and flange and elbow and so on.
Electrical accessories are those things which are used to detect
and monitor whole protective area and control whole system, also
warn people to evacuate and prevent from fire expansion.
These integrated three parts will be efficient to detect and
supervise and alarm and extinguish fire automatically.
Here attached below is complete composition of whole system
1. Choice for storage room, including ambient environment and
2. Design of pipeline, including placement of conduits and
3. Installation, integration of each parts and connection between