Chemical FM 200 Fire Suppression System Of 120L Type Cylinder
|2||Scale of Protective region for one zone||area:max single-zone is 800m² volume:max single-zone is 3600m³|
|6||Nitrogen Pressure of Driving Device||6.0±1.0Mpa(20℃)|
|7||Condition of reserving room for container||temperature: -10~50℃, relative humidity: ≤97%|
|8||max working pressure||8.0Mpa|
|9||min working pressure||4.6Mpa|
1. Multiple management in the control of the whole system
2. Agent quantity for biggest zone is enough to protect all zones
through selector valves
3. Direct target to expensive machine or delicate device
4. Short time discharge of extinguishing agent
5. Preparation for storage room
6. Space confirmation of placement for cylinder group
Electronic computer room, a data processing center,
telecommunications facilities, process control, expensive medical
equipment, industrial equipment, library, museum and art gallery,
clean room, anechoic chamber, emergency power facilities, flammable
liquid storage area, etc.
The place where the fire is easy to happen, like paint-spraying
production line, aging-electrical equipment, rolling machine,
printing machine, oil switch, oil immersed transformer, melt
impregnating tank, tank, large generators, drying equipment, cement
production process of pulverized coal, and the ship's engine room,
cargo hold, etc.
5.6Mpa Fm200 System Of 120L Type Cylinder is mainly composed by
three parts. Extinguishing devices and pipe fittings and electrical
Extinguishing devices are such things, like cylinder to fill and
store fm200, frame and driving device(nitrogen cylinder) to trigger
the storage cylinder to discharge agent and so on.
Pipe fittings are those conduits to connect extinguishing device
and guide agent into protective zone, like high pressure galvanized
steel pipe and flange and elbow and so on.
Electrical accessories are those things which are used to detect
and monitor whole protective area and control whole system, also
warn people to evacuate and prevent from fire expansion.
These integrated three parts will be efficient to detect and
supervise and alarm and extinguish fire automatically.
Here attached below is complete composition of whole system,